Tagor The circuit-breaker is caused to open automatically three times, the circuit being closed once by the auxiliary switch A and twice by the circuit-breaker itself. Utilities and manufacturing facilities use them: The history of standard IEC may have something to do with it. A direct current equal to 7 In is then passed through all poles, starting from cold. I am from India. IECwhich I introduced at length in the first of these blog postsgoverns CBs for industrial applications.
|Published (Last):||9 October 2012|
|PDF File Size:||1.21 Mb|
|ePub File Size:||5.15 Mb|
|Price:||Free* [*Free Regsitration Required]|
Tagor The circuit-breaker is caused to open automatically three times, the circuit being closed once by the auxiliary switch A and twice by the circuit-breaker itself. Utilities and manufacturing facilities use them: The history of standard IEC may have something to do with it.
A direct current equal to 7 In is then passed through all poles, starting from cold. I am from India. IECwhich I introduced at length in the first of these blog postsgoverns CBs for industrial applications. The opening time shall be not less than 0,1 s and not more than: The most suitable solution for use are MCBs certified with both standards as their performance meets requirements of use for residential installations and high enough for use in industry and infrastructure applications.
Reply Hello Jonas, No, your statement is not correct. Additionally, arrows indicating the direction of the current are allowed. In any case it will break 15kA. I am confused with two standards for the same breaker. Stil… 1 Can we say it is for industrial application if a MCB manufactured as per IEC only 2 According to these standards any manufacturers could provide life time warranty. The text of lEC Standard has been approved as suitable for publication as an Indian Standard without deviations.
More details you can find in my blogs about standard https: The alternating current shall have a substantially sine-wave form and the power factor shall be between isc and 0. Printed at Simco Printing Press, Delhi.
Compare those numbers to the V upper limit between phases for residential MCBs. Or take the tripping characteristics: Does it mean that the trip kA is different when the breaker is used for residential or non residential use? No part of these publications may be reproduced in any form without the prior permission in writing of BIS. Reply I have —2 working in the industrial sector and am having trouble completing test certs for installations fed from panels.
In addition, these circuit-breakers are then tested by performing simultaneously one O operation, with one circuit-breaker being inserted in each phase of the test circuit for three-pole circuit-breakers see figure 5. Review of Indian Standards Amendments are issued to standards as the need arises on the basis of comments. The information eic abefghi and 1 may be marked on the side or on the back of the device and be visible only before the device is installed.
Pollution degree 2, impulse voltage 4kV, isolation voltage is the same as nominal voltage Iwc. HI I would like to know iecc have been the design and technological trend in low and medium current and high current miniature circuit breakers.
Usually these circuit breakers sold by electrical retailers: I have never confused them yet maybe because its not much since I started working.
Reply Thanks for your reply. Mechanical and electrical endurance Test at reduced a. Kevin, You should keep it simple: This does not preclude the free use, in the course of implementing the standard, of necessary details, such as symbols and sizes, type or designations. The circuit-breaker shall trip in a time less than 0, 1 s.
The concept behind it as it evolved in ss was a single standard for all low-voltage switchgear. Reply Hello Lim, It is higher because of lower Icu breaking capacity ratio to service breaking capacity Ics, eg. Reply Good for making Technical specification for electrical tender. NOTE It is assumed that short-circuit currents of 1 A are not exceeded in installations In which, due to the loads connected, time constants in normal service up to 15 ms can occur.
Reply Kevin, You should keep it simple: Oec have started working in the industrial sector and am having trouble completing test certs for installations fed from panels. View Responses 57 Responses I am from India. NOTE This standard applies to circuit-breakers able to make and break both a. Addition at the end of the first paragraph: This standard gives additional requirements for single- and two-pole circuit-breakers which, in addition to the above characteristics, are suitable for operation with direct current, and have a rated d.
An MCB designed for indoor, pollution-free conditions would be woefully inadequate for harsh, outdoor applications that require pollution degree 3. Figure 18 — Examples of connections of the circujt-breaiiers in different d. Related Posts
They are both standards that specify requirements for low-voltage circuit breakers. Is there more in common? Which one if for homes, which one for industry? IEC , which I introduced at length in the first of these blog posts , governs CBs for industrial applications. They protect electrical power distribution of up to volts a. As for IEC , it relates to the a. The standard states that the top rated current is A, while the lowest is 6A and maximum value of rated short-circuit capacity Icn is 25kA.
IEC 60898-1 and IEC 60947-2: a tale of two standards